Wire Break Detection System
The system is used to find a wire and locate a break in a wire.
Das System consists of:
- Transmitter HG 80410
- Receiver HG 80420
- Antenna HG 80421
- The wire break detector is an electrostatic measuring device, the receiver has a limited range of approx. 10 cm.
- The conducting wires must be free of voltage. Crossing or parallel wires must be disconnected.
- If the lead to the conductor loop is made by twisted wires, the twisted part must be disconnected during the measurement.
- The point of interruption can only be found if the interruption is unambiguous (R -> ∞). A corresponding resistance measurement should be carried out beforehand. Insulation faults cannot be detected with the device.
Finding a broken cable is illustrated in the short description (PDF) attached below.
|Short Description HG_S-80400-B Rev. 01 (PDF)||168.43 KB||24.02.2023|